IEC 60551 PDF
IEC DETERMINATION OF TRANSFORMER AND REACTOR SOUND LEVELS. IEC Ed. Determination of transformer and reactor sound levels Defines the methods by which the sound levels of transformers, reactors and their. Find the most up-to-date version of IEC at Engineering
|Published (Last):||25 June 2007|
|PDF File Size:||4.95 Mb|
|ePub File Size:||8.60 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dewesoft power 60551 makes it easy to measure all the required temperatures winding, oil, ambient, etc.
The fans shall be safe kipping and separate protection by over temperature and magnetic equipments. General requirements for transformer 1. The core clamping structure shall not form closed loops and shall withstand a voltage, to the core eic tank, of not less than 2.
The fans groups shall design separate operation and independence to make sure two fans not stop at on. One of our specialists will get in touch as soon as possible. Assembly, testing and check before acceptance.
IEC | IEC Webstore
Standards The design, manufacturing, materials, testing of the transformers shall comply with General Technical Specifications, Special Technical Specifications and with the latest revision of the following IEC publications and Climate condition tropical: It shall be with max needles and with compensation functions.
Download our products and projects technical documents. Transformer testing Testing of power transformers makes a couple of different measurements necessary, which are described in the international IEC standard. Support type Sales and eic inquiry Dewesoft software support Hardware support Developer support Product feedback Other. Statement of demands and needs. The clamp assemble and structure shall be of a, non-magnetic type, and shall be effectively insulated and tightened so to ensure an even pressure on the whole core assembly and are not loosened by vibrations caused by transport and operation.
IV Factory Tests and complete transformers The following tests shall be carried out idc the Manufacturer’s works in the presence of the Employer’s Representative on transformers to be provided, in accordance with the requirements set out in IEC Publication No. HV bushing current transformers – Must be three secondary winding.
IEC | Determination of Transformer and Reactor Sound Levels | Document Center, Inc.
Three phases, three windings oil immersed and installation advertisement. The core shall be arranged suitable ducts for efficient oil cooling. Equipment used in testing must be certification quality by quality national. Radiator – The radiator shall be design and arrangement to enable easy cleaning and recover by hand. The cubicle fitted on control room. Dewesoft Dashboard Edit metadata. The Power quality module allows measuring harmonics of the voltage and the current up to some hundred kHz.
The plant shall be conform and supervision in during testing. Take the smart route to manage medical device compliance. The data can be represented in percentage of the fundamental frequency as required for the no-load current according to IEC standard.
Oil separate air by rubber envelope on conservator. Page 13 of 19 If content of document difference of contract, manufacture must to report and notice boar to compare of difference parts. The Power transformers are located, tests, sign on conform closed electrical and check and take over by professional of manufacture.
The cabinet fitted on the transformer tank. Degree of protection by enclosure: Page 7 of 19 – Equipment shall be provided supervision tap changers in times of step by step. After received request, manufacture supplies document corrected until approval by buyer.
Commitment to client-minded and product-fit approach is a crucial value.
Terminal and clamp out side used ACSR mm2 connector. No limitations for the values are given here. For more information check the power quality application page. Over voltage, under voltage protection. Current transformer used supervision HV winding temperature arrangement on B phase bushing.
Worldwide Standards We can source any standard from anywhere in the world. Transformers, Electric reactors, Cooling equipment, Air-cooled systems, Sound intensity, Acoustic measurement, Testing conditions, Noise environmentalMathematical calculations, Documents, Qualification approval. Page 5 of 19 Power supply for fans-motor: For each conservator a synthetic diaphragm ensuring an airtight seal shall be provided. The control cabinet shall contain: Both sides of each sheet shall be insulated with durable hot oil and heat-resistant baker enamel, varnish, or other chemical treatment, subject to the approval of the Employer’s Representative.
The Dewesoft power analyzer redefines analysis and testing process of the power transformer with its unique set of software tools and flexible hardware. Thanks for contacting us.
The steel ice be of thin laminations, annealed after cutting and rolled, to ensure smooth surfaces at the edges. All equipment accessories shall be sign and guide on operating and maintenance. After received letterwithin 05 days, buyer will be make answer by letter.